Sewer Line Repair In Tracy, CA
Responded to call from a homeowner regarding mainline stoppage. Technician Arrived to find cleanout in the backyard holding sewage. Recommended cabling mainline thorough the cleanout to clear. Recommended following with video inspection. Proceeded with cabling clearing line. Found multiple root intrusions in the main.
Recommended replacement of entire main from house to curbside cleanout, Approximately 70 ft. Client moved forward the recommendation and was very happy with services provided.
Dependable Plumbing Service
Call us today to book your appointment with your Local, Most Trusted, Top Rated plumbers in the area!
Project Type: Sewer Line Repair